40MVC / 38MVC. 40MVQ / 38MVQ. Service Manual. HighWall Duct Free Split System. Sizes To TABLE OF CONTENTS. PAGE. SAFETY. View and Download Carrier 40MVC product data online. High-Wall Duct Free Split System. 40MVC Air Conditioner pdf manual download. Also for: 38mvc. Manuals and User Guides for CARRIER 40MVC. We have 5 CARRIER 40MVC manuals available for free PDF download: Service Manual, Product Data.
|Published (Last):||3 April 2007|
|PDF File Size:||7.5 Mb|
|ePub File Size:||7.67 Mb|
|Price:||Free* [*Free Regsitration Required]|
Page of 35 Go. These compact indoor fan coil units take up very little space in the.
Conceal the tubing where possible. By pressing ‘print’ button 40mgc will print only current page. High wall fan coil unit condensate representative for drawings. If possible, display LEDs on both the indoor and outdoor units.
Compressor shall be fully hermetic rotary type. Enter text from picture: Don’t show me this message again. The fan coil is carriwr on the wall, near the ceiling. All connections between indoor and outdoor units must be as shown. Application Data If unit is exposed to strong winds it is drainage cannot be provided, unit should be equipped with recommended that a wind baffle be used.
Don’t show me this message again. Floor console 40mcc split system sizes 09 to 12 26 pages. High-wall ductless split system sizes to 40 pages. Got it, continue to print. Don’t have an account? If the installation location may be exposed to strong winduse a ends until all the connections are made. To print the manual completely, please, download it. Lift indoor unit into position and route piping and drain Do not form a rise.
The mounting plate should be located horizontally and level Indoor Unit on the wall. When adding air conditioning to spaces that are heated. Comments to this Manuals Your Name. Parts List Aa Aa Fig. Page 14 Catalog No: Enter text from picture: Safety Considerations Installing, starting up, and servicing air- -conditioning equipment These instructions cover the installation, start- -up and servicing of can be hazardous due to system pressures, electrical components, 38MVC,MVQ outdoor and 40MVC, MVQ indoor units duct free and equipment location 40mc, elevated structures, etc.
Remove field wiring cover from unit by loosening screws. Check with your Carrier representative to obtain Bend tubing with bending tools to avoid kinks and flat spots.
Carrier 40MVC User Manual
By pressing ‘print’ button you will print only current page. Carefully remove the mounting plate, which is attached to the back of the indoor unit. The fan coils are attractively.
Make sure that the drain tube slopes downward along its en- tire length. Page of 14 Go. Add to my manuals Add.
Carrier 40MVC Manuals
Floor console ductless split system sizes 09 to 12 26 pages. Table of Contents Add to my manuals Add.
Run interconnecting cable through hole 40mvv wall outside to inside. Installing, starting up, and servicing air- -conditioning equipment These instructions cover the installation, 40mvf -up and servicing of can be hazardous due to system pressures, electrical components, 38MVC,MVQ outdoor and 40MVC, MVQ indoor units duct free and equipment location roofs, elevated structures, etc.
Don’t have an account? This manual also for: Refrigerant Lines -in mm should be buried. Outdoor Unit Installation If the installation location may be exposed to strong winduse a ends until all the connections are made. Run interconnecting piping and wiring from outdoor unit to indoor unit. Mount outdoor power disconnect. Add- -ons to current space an office or cqrrier room. Ideal installation locations include: Comments to this Manuals Your Name.
Contact your Carrier accessory condensate pump. Failure to follow this caution may result in equipment 4.